ENVIROSERVICES & TRAINING CENTERS LLC
Ensure safe work conditions and prevent release of asbestos and lead during renovation activities at the Federal Building and US Post Office, 154 Waianuenue Ave, Hilo, Hawaii. Mobilized to the island of Hawaii. Provided oversight of asbestos related work for the 3rd Floor, rooms 302 to 305, including air monitoring and asbestos clearance testing. Asbestos clearance testing failed criteria and additional follow-up cleaning and testing is expected. Performed sampling and analysis of soil and thermal system insulation debris on bare soil to determine asbestos content. Debris contained regulated levels of asbestos. Soil in 2 of 4 sections contained detectable levels of asbestos less than 1 percent which is considered contaminated by Hawaii Dept of Health. Will provide design specifications for asbestos abatement if required. Further oversight activites are expected for lead related work and in different areas of the site.